<table><tr><th>From:</th><th>Richard Kahn</th></tr><tr><td>Sent:</td><td>Friday, February 6, 2015 7:48 AM</td></tr><tr><td>To:</td><td>Jeffrey Epstein</td></tr><tr><td>Subject:</td><td>Fwd: ZDC- Damage to RC High Voltage Line</td></tr></table>

Richard Kahn
HBRK Assoc=ates Inc.
575 Lexington Avenue, 4th Floor
New York, NY 1=022

Begin forwarded message:

Email details:

*   **From:** Brice Gordon
*   **Date:** February 5, 2015, at 8:17:32 PM EST
*   **To:** Rich Kahn
*   **Cc:** Zorro Ranch
*   **Subject:** ZDC- Damage to RC High Voltage Line

Rich
As discussed this morning

Y=sterday afternoon, Steve was trenching the new line from the Irrigation vau=t RC to Well 4, when he accidentally caught a high voltage feed to the Qwes= Microwave Tower.

This took out power to both the Quest Tower and=RC

Fortunately he just broke the conduit and pulled the Cable (pi= 3 & 4) from the pole (Pic 2) and the Junction box

## (Pic 1) located at t=e office

Carlos was spotting for him, but did not see the Cable i= time to stop Steve from lifting it with the backhoe. Please note=this line is not indicated on any As Built Plan for RC It was bur=ed approx 3 Feet in the ground, as apposed to the required 4ft Th=rs was no warning tape buried above the line to indicate buried electrical l=ne.

CNME was informed and came on sight to repair,=they had no record of this cable in there data base. They pulled the cable b=ck to both auction box and pole, replaced auction box terminals, replace tr=nsformer fuse on pole. Power was established at both location at 11.2= pm

This work took 5 1/2 hours to perform.

CNME will need to return to repair conduit, they intend to be back on sig=t tomorrow morning.

There will be charges for this=work, we will try and clarify these tomorrow.

## (Pic 1) located at t=e office (cont.)

=/div>

Brice Gordon=div>Stanley, NM

=div>