From: Ann Rodriquez

Sent: Friday, November 6, 2015 12:20 AM To: jeffrey E. Cc: Richard Kahn; Zorro Ranch Subject: Transformer: Mr. Felix Rey

Forwarded message From: Felix 5. Rey Date: Thu, Nov 5, 2015 at 5:04 PM Subject: RE: LSJE, LLC - November 5, <u>2015</u> To: Daphne Wallace

The 1500kva transformer was tested with TTR test. The B bushing on the transformer tested good but with high amps. The A bushing was tested and the D tap for that side of the transformer failed. We believe the 1500kva is much too large a transformer for the load that the island is using. Your meter at the site is showing less than 200am ps per phase. A 500kva is more a better size for the island at this point. As for the meter base we are still trying to get one.