<table><tr><th>From:</th><th>BMG &lt;</th></tr><tr><td>Sent:</td><td>Friday, April 27, 2012 8:53 PM</td></tr><tr><td>To:</td><td>Jeffrey</td></tr><tr><td>Subject:</td><td>Re: Libray</td></tr></table>

I got David from ARS out since they did install of dehumidifies

I noticed that the amount moisture coming off the cool and commented

Sent from my iPhone

On Apr 27, 2012, at 4:41 PM, Jeffrey <jeevacation@gmail.com> wrote:

> How did we discover?

>

> Sorry for all the typos .Sent from my iPhone

>

> On Apr 27, 2012, at 1:32 PM, brice gordon < > wrote:

>

» update on library system

>>

» 1. both dehumidifiers where down, one needs a new condenser the other

» had=was locked out and had to be reset

>>

» 2. It has been determined that only one recirculating pump should be on a= a time.

» when we commissioned the unit there was no mention at any time that

» we ha= to close this valve manual and rotate pumps monthly basic to much water passing over the coil to quickly.

- Trane did not even p=ck this up. !!

>>

>>

» new condenser will be ordered, this should be covered by warranty.

» Will g=t David to review controls for dehumidifiers so we can view in

» mechanical r=om since units are in attic space

>>

» humidity down to 67% and dropping

>>

>>

>>

>> Brice Gordon

» Little Saint James

>> USVI

>> Phone:

>>

<?xml version=.0" encoding=TF-8"?>
<!DOCTYPE plist PUBLIC "-//Apple//DTD PLIST 1.0//EN" "http://www.apple.com/DTDs/PropertyList-1.0.dtd">
<plist version=.0">
<dict>
</dict>
</plist>

<key>conversation-id</key>
<integer>218047</integer>
<key>date-last-viewed</key>
<integer>0</integer>
<key>date-received</key>
<integer>1335559909</integer>
<key>flags</key>
<integer>8590195713</integer>
<key>gmail-label-ids</key>
<array>
<integer>6</integer>
<integer>2</integer>
</array>
<key>remote-id</key>
<string>219726</string>

</dict>

</plist>