<table><tr><th>From:</th><th>jeffrey E. &lt;jeevacation@gmail.com&gt;</th></tr><tr><td>Sent:</td><td>Friday, February 26, 2016 3:39 AM</td></tr><tr><td>To:</td><td>Ann Rodriquez</td></tr><tr><td>Subject:</td><td>Re: Solar. Great St. James Stand Alone PV system</td></tr></table>

ok

On Fri, Feb 26, 2016 at 1:09 AM, Ann Rodriquez wrote:

Ann R.
Begin forwarded message:

From: ██████████████████████████████████████████████████████████
Date:=/b> February 24, 2016 at 2:52:07 PM AST
To: ████████████████████████████████████████████
Su=ject: Great St. James Stand Alone PV system

Afternoo= Ann,

After meeting with Danny and having a look at the existing stand alone=PV system I propose the following:

## Step 1;

Analyze and assess the present system to ensure peak performance and o=tput.

1) Test specific gravity of each cell in every battery. (This is norma=ly performed after "equalizing" the batteries to get the "b=st case" results. Once we open the batteries and get a preliminary in=pection we'll determine procedure)

	2) If equalizing is needed fill =ells and pulse charge to desulfate then check the cells

	3) Determine which batteries need replacing and build a map to track a=e and deterioration

	4) Check all cable and equipment connections and apply Nolox

	5) Test combiner box to ensure we have full output from each string of=the solar array

	6) Develop cost to bring system back to peak output

	7) Recommend site improvements to improve longevity and performance

	9) Discuss generator tie in and Auto Transfer Switch via existing Sunn= Islands charge controllers

10) Develop plan to interconnection needs to monitor and track system =hrough existing SMA Webbox. (connectivity required)

Cost of initial inspection and report (includes minifuses, Nolox, sulf=ric acid, and distilled water) Date proposed 2/29.3/01, 3 technicians, $1875.00

## Step 1; (cont.)

Step 2;

Repair and replace hardware as noted in initial report and quote

1) Batteries, cable, lugs, charge controllers, fuses, panels, groundin= configuration, etc.

## Step 3;

Develop hypothetical load and design modular Generation/Storage system=to provide scale

1) Site second system and develop cost outline using onsite machinery =nd resources

2) Evaluate existing T&D and propose upgrades

3) Propose alternate generation platforms if desired

## Step 4;

Continued online monitoring and monthly maintenance

1) Monitoring through online portal with response to alarms or "t=iggering" events (can be transferred to onsite person if desired)

2) Analysis of load juxtaposed with capacity will allow a more precise=expansion plan and increase

reliability

3) Monthly fee TBD (approx. $250)

Thank you for the opportunity. I've scheduled the initial work to =e performed next Monday 2/29, out of a sense of urgency. Please let me kno= your thoughts and contact me anytime with any questions.

Regards,

Bri=n Walden
Island Serv=ces Group, LLC
Pro=ect Management/ Energy Consultant
109=113 Castle Coakley, Ste #6
Chr=stiansted, VI 00820

=C2 please note

The information contained in this co=munication is confidential, may be attorney-client privileged, may c=nstitute inside information, and is intended only for the use of the ad=ressee. It is the property of

JEE

Unauthorized use, disclosure or co=ying of this communication or any part thereof is strictly prohibitedand may be unlawful. If you have received this communication in error,=please notify us immediately by return e-mail or by e-mail to jeevacation@gmail.com</=>, and destroy this communication and all copies thereof, including =11 attachments. copyright -all rights reserved

## Step 4; (cont.)