## Pumps P1 - P7

P1, P2, P3 - Cooling Tower pumps

P4, P5- Chilled Water pumps

P6, P7- Re Heat, Hot Water Pumps

Daily Schedule

1. Check pump pressure supply return.

2. Check pump seal for leaks (floor has leak detection).

Weekly Schedule

1. Check for bearing noise/seal ware.

2. Check pump gland for leaks in pump seals.

Monthly Schedule

1. Test for levels (by clarity chemical) in closed loop and open loop water systems, heating and chilled water.

Annual Schedule

1. Grease pump motor bearings, pump bearings. Note: Rebuild pumps as needed (we average two per year); send out to Argo General pump to re-machine all internal parts and seals.

"The information contained in this document is confidential and is intended only for the use of the authorized recipient. It is the property of Jeffrey Epstein. Unauthorized use, disclosure or copying of this document or any part thereof is strictly prohibited and may be unlawful.

©2013 Jeffrey Epstein - All rights reserved"

HOUSE_OVERSIGHT_009819
documents/HOUSE_OVERSIGHT_009819.jpg
{"people":["jeffrey epstein"]}