1. Eddy current test.

When Needed - Add oil.

## Cooling Towers

Daily Schedule

1. Check Condenser water temperature in and out; 10 Degrees Delta supply and return.

2. Check fan speed operation; fast and slow.

3. Check fill valve operation.

4. Check sump and water condition.

5. Open drain valve sump to blow down deposits that form in the sump.

Weekly Schedule

1. Check remote sump suction screen.

Quarterly Schedule

1. Tighten fan belts.

Six Months Schedule

1. Replace belts.

Note: See Operating and Maintenance Industries in owner's manual, section two. Proper chemical treatment is very important to keep the tower and chiller running trouble free.

"The information contained in this document is confidential and is intended only for the use of the authorized recipient. It is the property of Jeffrey Epstein. Unauthorized use, disclosure or copying of this document or any part thereof is strictly prohibited and may be unlawful.

©2013 Jeffrey Epstein - All rights reserved"

HOUSE_OVERSIGHT_009816
documents/HOUSE_OVERSIGHT_009816.jpg
{"people":["jeffrey epstein"]}