## Hot Water Re-Heat System

Bell & Gossett

HX1, HX2 heat exchanges -

Note: for maintenance check service manual next page; control set points and system from Landis BMS System, building office; Landis steam valve controls steam pressure to heat exchanger, see Siemens SKA Electronic Valve Actuator.

## Heating System

Daily Schedule

1. Check Supply and return temperature form BMS and unit on SC - level.

2. Check reheat pump discharge pump pressure 120 psi.

3. Check water make up PRV. For usage if valve is moist and wet. Make sure it is ni use showing link in system.

## Weekly Schedule

1. Check and open heat exchange shell; to blow down valve; condensate- if steam comes out, there is a leak.

## Monthly Schedule

1. Clarify water and check corrosion inhibitor levels in system.

2. Check steam inlets valves for proper operation at BMS and heat exchanger.

"The information contained in this document is confidential and is intended only for the use of the authorized recipient. It is the property of Jeffrey Epstein. Unauthorized use, disclosure or copying of this document or any part thereof is strictly prohibited and may be unlawful.

©2013 Jeffrey Epstein - All rights reserved"

HOUSE_OVERSIGHT_009822
documents/HOUSE_OVERSIGHT_009822.jpg
{"people":["jeffrey epstein"]}