The report details the service and repair work conducted by TSG on the SWRO plant at Little St. James Island. It includes incidents of pipe bursts and seawater exposure leading to damage of electrical components, membrane fouling due to foreign objects, and operational issues. The report outlines the steps taken to replace damaged components, clean and replace membranes, and address operational issues to restore the plant to its design parameters. Recommendations for further evaluation and training are provided.
documents/EFTA01109916.pdf
{}