TSG technical staff performed maintenance on the LSJ 90 K RO plant's high pressure pump. Issues included broken plungers, corroded gland nuts, and pitted valve recesses. Recommendations include replacing the fluid end assembly or considering a Danfoss axial piston pump/motor. Photos document the service trip and equipment condition.
documents/EFTA01109925.pdf
{}