The memorandum documents the reactivation and testing of Well 6 at Zorro Ranch, which was reactivated to compensate for the lost capacity of the Dakota well. The testing was coordinated by Balleau Groundwater Inc. and involved rehabilitation and capacity testing of Well 6. The well is capable of 15 gpm pumping for 10 hours a day, with a projected yield of 10 acre feet per year. Recommendations include replacing the existing pump with a 15-gpm pump and monitoring water levels to prevent dewatering of the production zone.
documents/EFTA01124856.pdf
{}