The memorandum documents the rehabilitation and testing of Well 6 at Zorro Ranch, which was reactivated to compensate for the Dakota well's lost capacity. The testing, coordinated by Balleau Groundwater Inc., found Well 6 capable of 15 gpm pumping for 10 hours a day, producing up to 10 acre feet per year. However, regional water level declines are expected to reduce yield over time. Recommendations include replacing the existing pump with a 15-gpm pump and monitoring water levels to prevent dewatering. Water quality analysis shows good quality, suitable for irrigation and drinking with treatment.
documents/EFTA00594361.pdf
{}